individual wires for continuity in the 60 Hz output wire
harness assembly (13217E4358).
Figure 5-44. 60 Hz output wire harness assembly.
d. Repair and Replacement.
(e) Replace connectors with defective or
(1) Repair wire harness and cable assemblies as
missing covers or any defect which would prevent
proper weather-seal of connector covers.
(a) Disassemble cable only as necessary for
(2) Replace receptacle covers that do not
provide proper weather-seal.
(3) Repair bent panel by simple shop repair.
(b) Replace wires found to be defective in
(4) Replace all other components found to be
tests (step f. above) or that were noted to be dam aged
defective through inspection or testing.
during inspection with wire in accordance with MIL-W-
e. Reassembly and Installation. Refer to TM
5086, Type II. Wire size and approximate length in
inches is provided in the wire run charts in the
illustrations referenced for testing.
5-30. Conditioned Air Temperature Control Panel
accordance with MIL-S-6872 using solder Type
SN60WRP2 per Fed Spec QQ-S-571.
a. Removal, Disassembly, Cleaning and Inspection.
(d) If self-clinching cable straps are
Refer to TM 5-6115-586-12 for instructions regarding
removed to facilitate repairs, replace them with new
removal and disassembly of the temperature control
cable straps at same interval and at cable breakouts.
panel, and cleaning and inspection of components.